Below is a picture of an explosion proof spot-type smoke detector installed in an electrical room in a parking garage. The detector is installed as per NFPA 72 126.96.36.199.1.
NFPA 72 188.8.131.52.1 – * Spot-type smoke detectors shall be located on the ceiling or, if on a sidewall, between the ceiling and 12 in. (300 mm) down from the ceiling to the top of the detector.
Looking for our NICET Fire Alarm System Exam Study Guides?
Level 1 –>> http://firealarmscertified.com/fire-alarms-systems-nicet-level-1-exam-study-guide/
Level 2 –>> http://firealarmscertified.com/nicet-fire-alarm-systems-level-2-study-guide/